Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
Both units switch on no heat or cold air
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Carrier air handler tonnage?
That is a fairly large difference. It is usually ok to have the inside evap. coil and blower up to 1 ton larger than the outside condenser. That will make the unit slightly more efficient as well as less likely to freeze up on low airflow situations. It is not recommended to install a new condenser on an old evap coil. There has been a lot of changes to the design of the coils in the last little while. For example a 10 year old 2 ton coil may only have 3 cubic feet of volume but a new 2 ton coil may have 4 cubit feet of volume.
There are many factors that may have infulenced the decision on what size condenser to install. Many of which can only be done by visiting the home and doing alot of work, checking the duct sizing bioth supply and return, inspecting the insulation and windows of the home etc. etc. Most of the time that never gets done. You can blame the contractor for not doing a complete check, but at the same time you can blame the customer because many contractors that are that good loose the job to a cheaper bid that did not no any of the research. It is a catch 22 for everyone involved.
There is ALOT more to sizing equipment that many people think, sadly that also includes many HVAC contractors. Way too many people use "rule of thumbs" or flat out "guess".
Sorry for the rant but your queston can only be answered by a good well educated HVAC contractor visiting your home. That type of a contractor is getting hard to find these days in such a price competetive world.
Posted on Oct 14, 2008
this is sign of low freon. you have a leak and ice is clogging the interior coils so little or no aire can pass thru it. Cut it off and find the leak.
Posted on May 04, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
Dec 03, 2016 | Carrier Heating & Cooling
Jan 15, 2016 | Carrier Heating & Cooling
Jan 30, 2010 | Ruud Heating & Cooling
Dec 28, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 22, 2009 | Carrier Heating & Cooling
May 02, 2009 | Carrier Heating & Cooling
Jan 05, 2009 | Carrier 38CKC042 Air Conditioner
Jan 05, 2009 | Heating & Cooling
Dec 02, 2008 | Heating & Cooling
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: