Question about Beverage-Air MT27 Beverage Cooler Commercial
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: bev air cooler
Bill, the main reason I've noticed for higher than normal temps in these boxes is filthy condenser coils (this will affect pressures in your sealed system). Remove the front lower panel and inspect your coils. Use a coil brush or a dust broom to thoroughly clean them up, don't use water. You can also pick up some condenser coil cleaner in a spray can from your local appliance parts store, but it's not necessary (the fumes are strong and may be objectionable to your customers... it gets 'em really clean, though!) After cleaning the coils, allow 24 hours for temps to stabilize. If they don't, here is a site for Beverage-Air, contact your local servicer with you exact model and serial number for pressure specifications. http://www.beverage-air.com/technical.service.html Hope this helps! Let us know, will ya?
Posted on Aug 13, 2007
You would need to be a certified refrigeration technician to even buy R-12, since it is a CRC refrigerant. The kegerator probably doesn't have service ports so you would either have to braze a low-side port in or use a piercing valve, and fix wherever the refrigerant leaked out from. Basically, by the time you pay a refrigeration tech to do all this, it isn't worth it and you would be better off buying a new one
Posted on Jul 26, 2009
this site has your manual and the manual has wiring diagram.
also has some common trouble shooting questions and answers.
Posted on Jul 11, 2010
Normally thermal overloads have a button like appearance on the compressor. Designed to open circuit when temp has caused distortion to the bi-metal contacts. Upon cooling will close again. Disconnect power before checking continunity on the overload terminals.
Posted on Nov 18, 2011
Tips for a great answer:
Sep 26, 2016 | Danby Silhouette Dual Zone DWBC14BLS 13.90...
Dec 28, 2015 | Beverage Air Refrigeration DD58C-1-B - 59...
Jul 18, 2012 | Refrigerators
Dec 31, 2010 | True TBB-2 Beverage Cooler
Aug 14, 2010 | Haier HC125FVS Wine Cooler Beverage Cooler
Apr 19, 2010 | Beverage-Air Kegerator - Beer Keg Cooler...
Oct 25, 2009 | Beverage-Air Kegerator - Beer Keg Cooler...
Jul 24, 2009 | Kitchen Appliances - Others
Jun 20, 2009 | Beverage-Air Kegerator - Beer Keg Cooler...
Jan 20, 2009 | Beverage-Air Kegerator - Beer Keg Cooler...
191 people viewed this question
Usually answered in minutes!