Question about Intermatic Hardware & Accessories
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Shut off breaker to you water heater. STILL TEST FOR VOLTAGE BEFORE YOU TOUCH ANY WIRING. The 3 wire that go to you water heater disconnect them. You are going to install them to your WH 40 timer.
The wires that you disconnected will now go to terminals: Black to Terminal 1 & White To Terminal 3, The Ground copper wire will go to the ground terminal should be a green screw.
You will have to buy some 10/2 wiring to go from your timer to your water heater. You can buy it by the foot at Lowes. Figure how much you will need.
With the new 10/2 wire install the Black to terminal 2 & White To Terminal 4, the ground wire will go to the ground screw with the other ground wire.
Wiring that went to terminals 2 & 4 will be installed to you water heater, the same way when you disconnected them. Set your timer clock and your done. Turn breaker back on!
Posted on Jan 28, 2009
yes u will, but u will have to make sure one of the motor wires are hooked up that way also, in case it has been moved, here is a link with the diagram u need
Posted on Aug 21, 2009
reading the specs i should say its a timer for only one zone. you can use it for one zone switching or for the pump. sorry.
Posted on Feb 14, 2010
Tips for a great answer:
Jun 10, 2015 | Intermatic Timer T40004RT3 300 Watt Pool...
Oct 06, 2011 | Intermatic T103 Indoor 120-Volt 40-amp...
Jun 12, 2011 | Intermatic T103 Indoor 120-Volt 40-amp...
Dec 19, 2010 | Intermatic & Indoor/Outdoor Rain Tight...
Nov 18, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Jun 11, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Mar 21, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Dec 24, 2009 | Intermatic T103 Indoor 120-Volt 40-amp...
Oct 01, 2009 | TORK Digital Interval Timer Ssa100r-24
Dec 12, 2008 | Intermatic T103 Indoor 120-Volt 40-amp...
167 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: