Question about Refrigerators
Please ASAP, otherwise my refrigerator inside of garage will die, too hot. Thanks a lot guys.
It appears that it is a "25" error. This is a "PFC" error. One of the circuit boards has failed. You could try a full power reset by turning the machine off at the power supply for at least 30 minutes and then trying again.
Posted on Jun 16, 2019
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
A few basic principles for air conditioner troubleshooting. For both central home air conditioner or window air conditioner,
the first thing to check is whether the unit is getting proper power.
If the unit uses 220 volt power be sure that the proper voltage is
getting to the unit. Same for 110 volt units. A voltage meter can be
used to assure that the voltage is correct.
For window air conditioning units the voltage can also be checked before and after the thermostat. If voltage is being supplied to the thermostat but not from it then the thermostat probably needs replaced. This is a fairly common problem. Another place to check is the fan motor voltage. The fan on window air conditioners runs both the indoor blower and the condenser fan. If that motor fails than the compressor may run for a short time, but will overheat and shut off. Continued operation like this will result in compressor failure. This motor can be economically replaced for larger window air conditioners, but for smaller ones the cost of replacement will be more than a new unit.
Central air conditioners for the home are more complex and there are more things that can go wrong. As with the window air conditioner the thermostat can also be a problem. The central air conditioner thermostat will only have 24 volts going to it. So don't look for high voltage there. Some units the voltage will be coming from the outdoor unit and others the voltage will be supplied by the indoor air handler or furnace. Most home central air conditioning will be supplied by the indoor air handler or the furnace. If the air conditioner is for cooling only the unit will usually have only two wires going to the condenser unit. Make sure that you have 24 volts across those wires.
The next thing to check will be the indoor blower. If your thermostat is calling for cooling then the indoor blower should be running. If there is no air moving across the indoor cooling coil then you will soon have a big block of ice formed on the coil. This can happen for a few reasons. The indoor blower is not working, the air flow is restricted and not allowing air to move across the coil. A clogged air filter would also do this. Or the outdoor condenser unit has lost the charge of refrigerant.
Finally and worst of all is when you have a complete compressor failure. Often when this happens the compressor will "lock up" or not be able to turn when power is supplied to it. Overheating or lack of lubrication are usually the main causes of compressor failure. Overheating can be caused by the outdoor coil around the compressor getting clogged with dirt, leaves, or grass. Loss of the refrigerant charge will also cause the compressor to overheat. It is the cool return gas coming back to the compressor that helps to keep it from overheating.
As you can see there are many things that can go wrong with an air conditioner and I have not come close to exhausting the possibilities here. I have just touched on the most common problems in a very basic way.
There are some basic trouble shooting things that can be done very easily. Most problems are above out of the range of comfort for many homeowners and professional help should be consulted before any attempt is made at repairs. Remember also, that the release of refrigerant gases into the atmosphere is a federal offense in the US. Proper care must always be taken to minimize the release of any gases. A license is also required to handle refrigerants. Make sure that the professional you call has the proper certifications to handle refrigerants properly.
Posted on Jun 07, 2011
the manual said that error code is cause of discharged thermistor..
-The detection value of the discharge thermistor is either open or shorted > Compressor, outdoor fan: OFF (automatically
releases when the value is returned to normal)
-Check the thermistor resistance values (refer to thermistor value chart)
-controller pcb defective...
Or try to click this link to see the diagnosis:
Hope it helps..
Thanks for using fixya..
Posted on Aug 12, 2011
SOURCE: Fujitsu asu24cl blinking lights
This machine is a looser. Mine has same blink codes. Its been serviced every year since it was installed 3-4 years ago.. Since the elctric work was half the cost of installing it, maybe Ill put in a differnt brand!
Posted on Oct 28, 2011
just happen to me, call the service guy........... he told me to cut power for 30 minutes cause it erase memory inside machine. I did and its working........ So happy
Posted on Jan 05, 2012
Tips for a great answer:
Nov 17, 2016 | Fujitsu Heating & Cooling
Jul 11, 2015 | Heating & Cooling
Nov 26, 2013 | LG Heating & Cooling
Feb 15, 2013 | Fujitsu ASU18RLQ Single Zone Wall Ductless...
Jan 24, 2013 | Fujitsu 24C1 Air Conditioner
Dec 27, 2010 | Fujitsu 24C1 Air Conditioner
Jul 04, 2009 | Fujitsu 24R1 Air Conditioner
Jun 16, 2009 | Fujitsu Plasmavision 42" TV
36 people viewed this question
Usually answered in minutes!