Question about Generac Electrical Supplies
You can use a ATS ( automatic transfer switch).
TS (automatic transfer switch) is mainly used in emergency power supply system to automatically switch the load circuit from one power source to another (standby) power source to ensure continuous and reliable operation of important loads. Therefore, ATS is often used in critical power supply places, and its product reliability is particularly important.
Posted on Aug 16, 2019
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I have solved the flooding problem . unfortanetly you must remove the carb to fix it. once you remove the carb you need to remove the fuel bowl. In the bottem of the fuel bowl there is a electronic seloniod that controols the amount of fule going to combustion. this aria had varnish and gunk built up around the plunger of the selonoid, long story short clean this out with carb and chook cleaner and put it back together. start her up and she will run like a champ.
Posted on Apr 27, 2009
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
Sounds like the electritian wired something wrong. Control wiring for that generator should be:
N1 and N2 = 240 vac utility input
Wire 0 = ground
Wire 194 (15B) = + battery
wire 23 = transfer signal
Posted on Oct 30, 2009
Tips for a great answer:
Jun 28, 2016 | Generac Electrical Supplies
Jan 21, 2016 | Electrical Supplies
Oct 07, 2015 | Generac 5975 GP5500 GP Series 5500 Watt...
May 05, 2013 | Generac 13,000 Watt / 13,000 Watt Home...
Dec 19, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
Sep 08, 2009 | Generac 100 Amp 120/240-Volt Transfer...
Aug 20, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
Jun 20, 2009 | Generac Guardian Ultra Source 15,000 Watt...
Mar 29, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
35 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: