Questions & Answers
Unsure if that is a refrigerator or an Air Conditioner.
Please add information to your question as to the model, or whatever you can tell.
198 views | 0 helpful votes
Compressor turns on and runs for about 1 min then
First replaced the thermostat then check on condenser unit that's outside .make sure the fan is running when compressor runs .if not there is your issue .If fan runs and compressor keep shutting off you might have a dirty coil so clean it out with water or you might have a leak in the system causing unit to shut off on low pressure .if this is the case you need to call a service technician .
Try simple things first like clean coil ,capicator and fan operation.
1,228 views | 0 helpful votes
How do i wire analog thermostat to digital
You need to get a different thermostat.you can change an analog thermostat to digital, but you have to replace the motherboard with a digital compliant one. You can't just change the thermostat. Your best bet is to put back the old thermostat or upgrade to a different compatable thermostat
636 views | 0 helpful votes
My a/c duo-therm model #57915331
Go to your heater and locate the circuit board inside. There is a 3 amp fuse that protects the board and it is a regular auto fuse and isn't made for any surges in the system. When you turned your generator on with the system on, chances are you surged the system and that fuse went. Breakers allow for surges where fuses don't
358 views | 0 helpful votes
Duo-Therm compressor does not turn off
I think you checked voltage across the run capacitor, the brown and white wires. The voltage to the motor would be on the black and white wires And inside the motor, a thermal protection device opens the black wire, leaving no potential voltage to the other voltage line nor capacitor line ( brown and white are the same line).
The solution, varify that the motor is wired correctly, then that the capacitor value is correct, not weakened, that the motor vent holes are not blocked or obstructed, that the motor amps are not exceeded, that the motor bearings have no side play and not worn.
Before replacing the motor, make sure the wiring is correct, the motor and capacitor are not good.
511 views | 0 helpful votes
Model # 57915.622 Installed new
It is possible that a sudden loss of power caused the fan to run backwards. Usually that happens to a compressor, not a blower but I can't think of any other reason. May consider installing a time delay (delay on break), right on the red to the tstat rather than yellow, to ensure everything is included in the delay. Most newer tstats have them built in, possibly upgrade tstat.
If you need further help, reach me via phone at https://www.6ya.com/expert/thomas_092728000e6acb79
51 views | 0 helpful votes
Not finding what you are looking for?