I just installed a honeywell 5-2 progammable thermostate.. Everything is hooked up fine and I have my days, hours wake, sleep, leave...etc all set, but when it goes on.. for example, I have it set for...
You didn't include a model number, so it's hard to know for sure - but I'll take a stab at this one. Many of these t-stats have a programmable offset to reduce "hunting". This can be as little as 1 degree or more than 2 degrees.
This means if you set the offset to 1 degree and the room temperature to about 65 degrees, the furnace will heat the room until the t-stat registers a rising temperature of 66 degrees. The furnace shuts off and will not turn on again until the t-stat registers a falling temperature of 64 degrees. The average is 65 degrees, and prevents the furnace from starting and stopping numerous times instead of just once with the 1 degree offset.
You can further reduce the number of furnace start and stops by increasing the offset to 2 degrees. This would work like this when the t-stat is set to 65 degrees and the room is cool:
Room Temp Furnace
The room is now warm and heat or furnace is off. The room begins to cool like below:
With a 1 degree offset, the room temperature varies +/-1 degree (about 2 degrees total). With a 2 degree offset, the temperature about varies +/ -2 degrees (about 4 degrees total).
Also, when the thermostat shut the heat off, the heat that was made is delivered to the space instead of wasted by sending outdoors - so the room will get a little warmer even though no fuel is being burned. The same holds true at the other end. When the t-stat turn heat on, fuel is burned, but there's little heat until the source has reached the optimum temperature and then the heat is delivered to the space.
I hope this helps & good luck! Pleas rate my reply - thanks!
Jan 24, 2011 |
Honeywell Programmable Thermostat Heater