Question about York Furnace Draft Inducer Blower Fasco # A224
Heater comes on but the blower shuts off after 30 seconds and then 15 seconds later it comes back on after 30 seconds it shuts off again . After three tries I get a error code 4 blinks then the heater comes on and the same thing happens all over again.After 10 minutes of this the blower will come on and stay on.I turn the heater down at night and when I turn it up in the morning the same thing happens all over again.
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I had the identical problem with my York. Problem was the burners. The heating element would light the first burner but the flame wouldn't move to the other burners. The flame sensor didn't detect a flame on the last burner so the gas valve would shut off. I removed and cleaned the burners then reversed the first and last.
Posted on Dec 17, 2009
Check gas pressure, inspect manifold & make sure there is not a blockage.Make sure gas is present and main gas shut off valve to furnace is on also check the knob on the 24 volt gas valve and see if it is in the on position , check the MV terminal on the gas valve to 24 volt common with a volt tester to see if you have 24 volts present, if you do have 24 volts at gas valve, replace valve. if you do not have 24 volts at gas valve check high limit control & roll out limits for a open circuit, Good luck.
Posted on Mar 04, 2010
The furnace is not sensing the flame. Turn off the power.
There is a metal rod in front of the last burner to light. It is corroded and needs to be cleaned. Its the flame sensor .
take the 1 screw out holding it in to the bar and scrub it with some steel wool till shiny. replace and turn on furnace. all should be fine.
Posted on Apr 04, 2010
Tips for a great answer:
Jan 03, 2016 | Heating & Cooling
Jan 17, 2015 | Williams Heating & Cooling
Dec 16, 2009 | Goodman GMS90703BXA Heater
Dec 12, 2009 | Heating & Cooling
Dec 01, 2009 | Goodman GMS90703BXA Heater
Jun 09, 2009 | Coleman Propane Forced Air Heater...
Mar 06, 2009 | Pentair MINIMAX NT TSI IGNITER
Nov 20, 2008 | Heating & Cooling
Nov 25, 2007 | Heating & Cooling
Nov 18, 2013 | York Furnace Draft Inducer Blower Fasco #...
224 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: