Question about York Furnace Draft Inducer Blower Fasco # A224
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Check gas pressure, inspect manifold & make sure there is not a blockage.Make sure gas is present and main gas shut off valve to furnace is on also check the knob on the 24 volt gas valve and see if it is in the on position , check the MV terminal on the gas valve to 24 volt common with a volt tester to see if you have 24 volts present, if you do have 24 volts at gas valve, replace valve. if you do not have 24 volts at gas valve check high limit control & roll out limits for a open circuit, Good luck.
Posted on Mar 04, 2010
Tips for a great answer:
Aug 06, 2013 | Saeco Vienna Plus Espresso Machine
Jul 05, 2011 | Computers & Internet
May 24, 2011 | York Barbell Home Use Fold-Up Treadmill
Apr 28, 2011 | Cell Phones
Jul 26, 2010 | York Exercise & Fitness
Feb 20, 2010 | York Furnace Draft Inducer Blower Fasco #...
Nov 28, 2009 | York Furnace Draft Inducer Blower Fasco #...
Dec 27, 2008 | York Yankees Bedding MLB Comforter
Nov 18, 2013 | York Furnace Draft Inducer Blower Fasco #...
66 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: