Question about Ruud Heating & Cooling
If the inducer motor is not turning on, it is not getting a call for heat and the hsi should not be energized. If it is energized without a call for heat, then the circuit board will need to be replace in the furnace...it has stuck contacts on the hsi relay.
Posted on Jun 27, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Remove at least one of the wires going to that solenoid on the gas valve. Check for continuity between the 2 legs of the solenoid. If you cannot get a reading then you have a bad valve. If you indeed do have continuity start the furnace and see if voltage is going to the valve. If you have no voltage going to the valve then you could have a bad board. If voltage is going to the valve then the gas valve has failed internally or you ain't paid the gas bill. LOL.
If you need further help, reach me via phone at https://www.6ya.com/expert/dan_73bbd84fe1d95b61
Posted on Jan 06, 2012
Tips for a great answer:
Jan 06, 2018 | Ruud Heating & Cooling
Oct 23, 2016 | Ruud Heating & Cooling
Jan 06, 2012 | Heating & Cooling
Mar 22, 2010 | Ruud UBHC Air Conditioner
Mar 03, 2010 | Ruud Matching Split Air Conditioner
Jan 09, 2010 | Ruud Heating & Cooling
Dec 21, 2009 | Heating & Cooling
Jan 04, 2008 | Heating & Cooling
67 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: