Question about Dometic Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Carrier thermostat
I hate to say it but Ive had trouble with Carrier's Tstats doing similar improper things. Unfortunatly the only repair is going to be replacement of the whole tstat. I recommend Honeywell's FocusPRO or VisionPRO tstat. Ive yet to have one fail and they have a 5yr warranty if they ever do.
Posted on Nov 26, 2007
Whats the amp breaker? Is this for the inside unit or the outside condenser? If the inside and gas heat you have a bad fan motor, If its an electric furnace , the same, but if its the outside unit, the fan could be going bad, locking up and the compressor still runs and pulls high ampsand tripps breaker or the compressor is just pulling too many amps due to plugged coils with dirt , grass or weeds blocking airflow.(firstname.lastname@example.org)
Posted on Jun 09, 2008
open the service panel to check for control voltage of 24volts when tstat calling, The contactor should be pulled in, if contactor is down,and contacts appear to be clean, and the unit is still not running, it is a bad compressor. to test this unplug the black wire from the compressoror at contactor,w/ power off! Turn on power if fan works normally it's a bad compressor. However if you see a swollen split cap(5 wires to a soup can looking w/ the terminal C,F,and Comp), switch it first and start at square one.
You also need to consider the high pressure switch if its cycling on off on off.
Posted on Mar 12, 2009
SOURCE: Ruud AC fan won't shut off
it sounds like this is an electromechanical system, (no circuit board) verify that you wired the normally open switch at the fan limit control to the low speed fan, to the normally closed on the relay..(series circuit) if either of these are wrong the fan will runn all the time
Posted on Jul 12, 2009
Tips for a great answer:
Jul 02, 2018 | Dometic Heating & Cooling
Jul 25, 2017 | Dometic Heating & Cooling
Nov 01, 2015 | Heating & Cooling
Jun 09, 2014 | Dometic 3313189.000 White Single Zone LCD...
Jul 05, 2013 | Dometic 3313192.000 White Single Zone LCD...
Sep 18, 2012 | Dometic Rooftop RV Air Conditioner
Jun 06, 2012 | Dometic Rooftop RV Air Conditioner
May 04, 2011 | Dometic Rooftop RV Air Conditioner
58 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: