Question about Intermatic Hardware & Accessories
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
To download the file you need Acrobat reader 7 at least. I just tried it and I was able to get it. It was slow but got it. Go for it and hop this was helpful!
Posted on Aug 23, 2009
That circuit breaker is letting you know that you've got a problem in the electrical wiring.... What's next is to turn the power off to BOTH legs of the breaker.
Begin by physically inspecting all the connections in the timer box, and at the breaker and all the way to the pump motor. Make sure all connections are dry, and there's no water in any of the conduits...this will cause a short circuit and trip the breaker. If there's any bare power leg wires touching a grounding point , this can cause the breaker to trip. Lastly check the motor on the pump; on the motor end, there should be a cap you can remove and use a crescent wrench to make sure the motor shaft is moving freely. It could be jammed with debris....this happens around my pool often because I'm surrounded by trees with needles. If the motor cannot turn freely, this will cause the breaker to blow... I'm pretty sure that your timer isn't the issue... Please let me know what you find out.
Posted on Nov 19, 2009
My first thought would be to make sure that there is power to the timer, 120 volts. Then I would check the wiring for the lights. then I would check the output of the timer with a voltage meter looking for the 24 volts.
Please vote !!
Posted on May 12, 2010
EI600 is a heavy duty 20Amp in-wall timer that is battery operated, and can replace single-pole or 3-way switches.
Posted on Nov 09, 2010
Manual override lever is good overall test of T101 120Volt timer.
T101 timer has 3 terminals: A 1 2
See wiring diagram on following link:
Electricians test, they don't guess.
So test your wire:
Separate all wires for testing.
Use ordinary 2 prong tester.
Tape wood sticks to tester leads to keep hands away from power.
Stand on dry boards. Do not hold or touch anything metal.
Turn power ON.
Test each wire to bare ground wire.
Tester lights up on Hot wire. 120V circuit has only 1 Hot wire. If you have 2 Hot wires, you might have 240Volt circuit and need T104 timer. If circuit has 1 Hot wire, then that Hot wire must connect to terminal 1.
If you have NO Hot wire, then check circuit breaker.
Hot wire is identified.
Now test Hot wire to all other wires, except bare ground wire.
Tester lights up on Neutral wire. Neutral wire must connect to terminal A.
If you have NO Neutral wire, then additional wiring is needed, or circuit needs further testing to see what type of wiring you are working with.
Bare ground wires connect to green ground screw.
Notice there are small white wires also connected to terminals A and 1. These small white wires power the 120V clock motor. With Hot on terminal 1 and Neutral on terminal A, the clock motor will run, and yellow dial will rotate.
If timer dial does not rotate after connecting Hot ans Neutral, then test voltage across Hot and Neutral to make sure it reads 120V.
Your circuit should have 2 wires remaining.
These wires go to 120Volt load (fan, light, motor)
Connect these two wires to terminals A and 2.
Try manual override.
If Load turns ON-OFF, then timer is wired correctly.
If Load does NOT turn ON-OFF, then reverse Load wires on terminals A and 2.
Add a comment any time.
Posted on Dec 28, 2010
Tips for a great answer:
Dec 04, 2012 | Hardware & Accessories
Aug 13, 2011 | Intermatic ET70215C Electronic Energy...
Aug 05, 2011 | Hardware & Accessories
Jul 16, 2011 | Intermatic Inc. EJ500C Digital Wall Switch...
Apr 18, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
Mar 09, 2011 | Intermatic Timer T12404R Pool & Spa...
Jan 03, 2011 | Intermatic 24 Hour Electronic Timer
Dec 30, 2010 | Intermatic EI210 Electronic Auto Shutoff...
Oct 06, 2010 | Intermatic & Indoor/Outdoor Rain Tight...
Jul 19, 2010 | Intermatic R8806P101C -...
103 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: