Question about Hardware & Accessories
Does your wiring look like what is shown in the instruction papers?
From your description, it does not sound like it. There is no white wire attached to the switch.
What type of bulbs are you connecting to? These require bulbs that can pass small amounts of current when off == incandescents and florescent. They may not work with LEDs.
Posted on Oct 04, 2019
You need two switches. It sounds like the Electrician set up the junction box for two circuits(Lights and Fans). i say this because your supply has 4 wires, Red , Black, White and Bare. We may be able to oversome this with one Lutron Switch. Allow me to investigate, and I will be back.
Posted on Oct 29, 2007
Look on the relay for the terminal numbers.
Terminal 30 goes to the battery positive.Red Wire
The two terminal 87 go to the fog lights.Black Wires
Match the color wire with what you have on the relay connection for the rest of the wires.
Terminal 86 should connect to your low beam headlight.
Terminal 85 should go to the fog light switch.
The fog light switch should connect to the terminal 85 and the other terminal on the switch will connect to ground.
Posted on Feb 04, 2010
remove white switch one and connect to incoming white ground--all whites should be connected [hooked] together these are grounds-- switch 1 black from fan ,leave switch 2 red from fan ,switch 3 vanity black
Posted on Feb 22, 2010
OK .. the thick black and white are the power for the fan , are there also white wires on the lamp sockets ..??
The thick black wire should connect to the black wire on the switch.
The small black wires connect to the red and blue wire on the switch .. two small black wires each .. that should give you a position for 2 lights , and 4 lights, on the step switch .. but there should be white wires from the lamp sockets connected to the thick white from the fan .
please respond .
Please Vote !!
Posted on May 25, 2010
Testimonial: "I appreciate the response, which reinforced my thought process and it worked - Thanks!"
The usual connection for this type timer is the house black power to the timer black, the house white power to the timer white and the , the light black wire to the red timer wire.
If you only have two wires, one black and one white, at the switch location, then you cannot use this style timer , as it needs a neutral. You should return this timer and get one that does not require a neutral connection.
Please Vote !!
Posted on Jun 01, 2010
Tips for a great answer:
Dec 10, 2016 | Cars & Trucks
Jan 16, 2016 | Electrical Supplies
Apr 01, 2013 | Leviton ODS10-ID Decora Wall Switch...
Sep 07, 2011 | Leviton ODS10-ID Decora Wall Switch...
Jan 08, 2011 | Columbia Telecommunications Group...
Jan 05, 2011 | Leviton ODS10-ID Decora Wall Switch...
Nov 28, 2010 | Leviton R01-PR180-1LI Decora 180 Degree...
Dec 01, 2008 | Intel Pro PC Camera CS430 Webcam
75 people viewed this question
Usually answered in minutes!