Question about Manitowoc Kitchen Appliances - Others
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Whats the amp breaker? Is this for the inside unit or the outside condenser? If the inside and gas heat you have a bad fan motor, If its an electric furnace , the same, but if its the outside unit, the fan could be going bad, locking up and the compressor still runs and pulls high ampsand tripps breaker or the compressor is just pulling too many amps due to plugged coils with dirt , grass or weeds blocking airflow.(firstname.lastname@example.org)
Posted on Jun 09, 2008
check for fuses in disconnect at the out door unit or a reset button where the copper line set goes into the unit at make sure stat wires have not been damaged hope this helps
Posted on May 15, 2009
The compressor is probably drawing to many amps. Breaker could be weak also.. Need to check the amp draw on the compressor.
If the breaker is hot when it blows, the compressor is probably going bad.
Posted on Jul 27, 2010
This sounds like you will have to replace the logic board. Whether you repair or replace get a surge protector 900 joules or higher unless you want it to happen again. You can get replacement parts at searspartsdirect.com. Thanks BB
Posted on Sep 03, 2010
The unit shuts off based on the magnetic reed switch in the plastic curtain on the front of the evaporator. If the ice is not falling as one single sheet with about 1/4"-3/8" of a bridge conecting all of the cubes then the ice is too thin. When the ice falls (in a single sheet of ice) if there is enough ice in the bin to hold that ice up and keep the curtain open the unit shuts down. A full bin may only be what appears to be 2/3 or 3/4 of a bin full because the ice sheet is propped up behind the curtain. If the ice sheet is too thin and does not fall as a single sheet more often than not a single cube or a piece of a cube can get caught between the curtain and the evaporator plate. This can shut the unit down for several hours until that piece melts and the curtain closes again.
Posted on Jan 04, 2011
Tips for a great answer:
Jun 30, 2018 | Washing Machines
Sep 19, 2015 | Manitowoc Ice Machine QD-0212A Air Cooled...
Dec 08, 2014 | Manitowoc QY0215W Self Contained 220Lb...
Mar 07, 2014 | Kitchen Appliances - Others
Sep 06, 2012 | Refrigerators
Jun 29, 2011 | Manitowoc - QD-0212A/115-1
Aug 05, 2009 | Manitowoc MAN-CVD2075 Condenser Unit...
Jul 15, 2009 | Goodman CKL36AR36 Air Conditioner
Jun 11, 2009 | Whirlpool ES5FHAXS Side by Side...
Mar 29, 2009 | Manitowoc Koolaire Undercounter Freezer...
29 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: