Question about UPM Programmable Wall Switch Timer
Posted by Anonymous on
You are replacing a single-pole switch that has two wires.
You posted under UPM timer.
But UPM timers have a red wire instead of a blue wire, so you have different brand.
Some GE programmable timers and some Leviton timers have a blue wire.
Here are instructions:
-Green wire goes to bare ground wire.
-Timer black wire goes to black wire
-Timer blue wire goes to white wire.
-Located in back of electric box are white wires twisted together and covered with wire nut. These are neutral wires. Timer white wire connects to these wires. This will power electronics inside the timer.
-If your box does not have white neutral wires described above, then connect timer white wire to bare ground wire along with timer green wire.
-Turn power ON, and push on-off button. If timer works, then it is wired correctly.
- If timer doesn't work, then reverse Timer blue and Timer black wires.
- If lights blink on-and-off, then you connected white wire incorrectly, review wiring shown above.
If your box does not have neutral wires or bare ground wire as described above, then buy Walmart.s Brinks 46-1022 or Intermatic ST01C or Intermatic EJ500 or Aube T1032. These timers do not need neutral or bare ground wire.
Posted on Jan 01, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Old timer: Intermatic EJ500 & ST01C timers have a battery. Battery operates the clock motor. Red wire is for 3-way circuit [a hallway with 2 switches is a 3-way circuit].
Utilitec timer, clock runs on 120Volt circuit instead of battery. So clock has to have power.
How to connect wires:
Black timer wire connects to hot wire from breaker box.
Red (or blue) timer wire goes to landscape lights.
White timer wire connects to white neutral wire [or if no neutral is available, connect to bare ground wire].
Green timer wire goes to bare ground wire.
How to find black hot wire and white neutral wire inside box: Disconnect and separate wires so you can test. Use ordinary tester. Power is on. There is only 1 black hot wire inside each electrical box. Test each black wire to bare ground until tester light comes on > that identifies the black hot wire. Next, test black hot wire to white wires until tester light comes on > that is the neutral wire. Exception: This test does not necessarily work with 3-way switches since they reverse each time switch is thrown.
Posted on Sep 21, 2010
HI .. if the switch has only a black and white wire attached, and there are no other wires in the wall box, then you cannot use this timer switch. You need to return it and get a timer that does not use a neutral connection. The wires you have are a switch leg from the light and there is a white wire but it is not a neutral.
If there are other wires in that wall box , tell me and we can chat more about how to remedy this .
Please Vote !!
Posted on May 25, 2010
SOURCE: Bought Utilitech 7 day Digital
Utilitec sells 2 different in-wall timers. Both wire the same.
Open following link for Utilitec wiring instructions.
Posted on Jun 18, 2011
Tips for a great answer:
Nov 22, 2012 | Hardware & Accessories
Dec 13, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Dec 11, 2010 | Woods Hardware & Accessories
Nov 16, 2010 | GE 60minute Automatic ShutOff Timer Switch...
Oct 17, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Sep 14, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Sep 04, 2010 | Intermatic Inc. ST01C Digital In-Wall...
May 24, 2010 | Leviton 1000W / 20A 1HP-120V - 6230M-I -...
Apr 08, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Dec 30, 2009 | Dryers
Apr 03, 2013 | UPM Programmable Wall Switch Timer
2,853 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: